|Posted by wilkinsoncc on June 25, 2017 at 3:55 AM|
Advice on what to do to reassure residents
Here is the current guidance for landlords in light of emerging findings from Grenfell Tower
If you discover that the cladding and insulation are of the same type used in Grenfell or fail the test then there are some emergency measures that you should immediately implement to ensure the safety of residents, pending replacement of the cladding
Notify Fire and Rescue Service.
Inform your local fire and rescue service fire safety/protection department. Failure to do so may put fire-fighters as well as residents at risk. The fire and rescue service will carry out an urgent inspection with the ‘responsible person’ to ensure that they are identifying and introducing appropriate interim measures, as set out below. The fire service will carry out a further inspection once the interim measures have been completed:If the building is protected by an automatic sprinkler system (or equivalent fire suppression system) you might not need to take any further interim measures before replacement of the cladding.
If the building is not protected by a suitable suppression system you must consider the need for interim measures. The measures adopted need to be based on an assessment of the risk by a competent person, but the following must, at least, be considered:
- Residents to be advised to ensure all smoke alarms are present and working in their flat; to report concerns about fire safety measures in the building (eg presence of combustible materials in escape routes) to their landlord and, understand the purpose of any interim measures being taken.
- Closure of car parks in which a vehicle fire could impinge on cladding.
- Provision of a temporary communal fire alarm system, comprising smoke detectors in circulation areas and plant rooms, and fire detectors (possibly heat detectors, rather than smoke detectors) in conjunction with fire alarm sounders in each flat. This will enable the entire block to be evacuated simultaneously in the event of fire. This option is unlikely to be suitable for tall blocks, in which a large number of people would need to use escape routes at the same time. The system may comprise a wireless system, using radio to link devices.
- Provision of a fire watch by appropriately trained patrolling security officers/wardens.
- In the case of the most serious risk, consideration must be given to moving all residents out of the block until satisfactory remedial work has been done.
Website ® WILKINSON CONSTRUCTION CONSULTANTS LTD Contact firstname.lastname@example.org
Company details Co Reg No 06808615 Vat Reg No 977 3745 63 Approved Inspector Building Control CIC Licence No 153
Reg Address 16th Floor Portland House Bressenden Place London SW1E 5RS D&B D-U-N-S® No 211518835